Central heating - hot water
Early hot water systems were used in Russia for central heating of the Summer Palace (1710?1714) of Peter the Great in Saint Petersburg. Slightly later, in 1716, came the first use of water in Sweden to distribute heating in buildings. M?rten Triewald, a Swedish engineer, used this method for a greenhouse at Newcastle upon Tyne. Jean Simon Bonnemain (1743?1830), a French architect, introduced the technique to industry on a cooperative, at Château du P?cq, near Paris.
However, these scattered attempts were isolated and mainly confined in their application to greenhouses. Tredgold originally dismissed its use as impractical, but changed his mind in 1836, when the technology went into a phase of rapid development.
Early systems had used low pressure water systems, which required very large pipes. One of the first modern hot water central heating systems to remedy this deficiency were installed by Angier March Perkins in London in the 1830s. At that time central heating was coming into fashion in Britain, with steam or hot air systems generally being used.
Perkins' 1832 apparatus distributed water at 200 degrees Celsius (392 °F) through small diameter pipes at high pressure. A crucial invention to make the system viable was the thread screwed joint, that allowed the joint between the pipes to bear a similar pressure to the pipe itself. He also separated the boiler from the heat source to reduce the risk of explosion. The first unit was installed in the home of Governor of the Bank of England John Horsley Palmer so that he could grow grapes in England's cold climate.
Checking the boilers working in a block of flats
Usually when putting a new unit for use in all apartments are mounted so the boilers operating on gas or electricity. The task plumbers will not only be mounted boilers in all apartments, but also a thorough check of their safety and to adapt their work to the accepted standards. The equal time derogation will also be checking the efficiency of the installed boilers and gas leaks associated with their work. Residents should report to the administration failures resulting in their boilers and replace them only on those that are admissible in blocks for security reasons. Building administrator may also instruct mandatory exchange of the boilers, which ceased to function well.
sewer cleaning methods in blocks
The blocks may be different failures sewage. Within a week, they are repaired by a team of plumbers employed in cooperatives. In contrast, during the holiday season, or in the case of sudden death during the night, residents will be able to call the emergency water and sanitation and ask to come to the block where the accident occurred. In some situations it may become necessary to purify the basement flooded by the sewage system before the tenants will be able again to enter it. Sewer block can be cleaned using methods commonly used to clean drains, such as. Pressure method. After her performance will be further tested patency sewage before residents return to their homes.